Home › Electrical Engineering Forum › General Discussion › Power Factor In Depth › Re: Power Factor In Depth

Dear Mr. Steven ;

First, it’s a good subject to be discussed but certainly not the principal basics as mentioned, because all Electrical Engineers should absolutely know it.

Let me please mention to the following points:

**Leading and Lagging Power Factor :**

- When mentioned “ Voltage phaser or Current phaser ” that means “
**Voltage Vector**or**Current Vector**” . - When you say “ we add capacitance to our system to minimize inductance and vice versa ”, you certainly mean that we add the capacitance to have a capacitive current that will minimize the inductive current ”.

**Active Power and Reactive Power :**

- The 2 formulas are mentioned to the “ Active Power ” where the 2
^{nd}should be :

“ **Reactive Power** : V(rms)I(rms)sin(angle between V and I) ”

- It’s mentioned that “ both inductor and capacitor (pure) are lossless elements means that
**they don’t consume any power they only cause voltage drop across themselves**”, but sorry to say : electrically it’s not right, because when there’s a drop voltage, that means there’s a current runs in the circuit, and if there’s a current that means there’s a Power’s consumption. By another wards:- All “ pure Capacitive or pure Inductive loads consume a Reactive Power ”.
- The Reactive Power is a kind of power without obtaining a useful work.
- It’s mentioned also that “ They only absorb power from the source
**and release it after wards**” and “ Thus Reactive power**oscillates**or**moves to and forth in the circuit**… ”, but sorry to say : electrically it’s not right, they absorb ( consume ) power but they don’t release it, and also the absorbed Reactive Power doesn’t oscillate or move to and forth in the circuit.

**Power Factor (Practically) :**

To be more clear, the relation between the “ Cos ϕ ” ( Power Factor for the Fundamental Voltage and Current ) and the Power Factor for Network containing Harmonics ( Polluted Network ) is done by the following formula :

**Power Factor = Cos φ / √(1+THD I²)**

Where the “ THD I ” is the Total Harmonic Distortion of Current.

So, relative to your formula the Distortion Factor is : **1/√(1+THD I²)**